Where there is no gas supply, or perhaps no desire for a boiler, instant hot water heaters provide an ideal solution, particularly for small businesses such as florists, beauticians, cafes and barbers.
One of the first questions to ask is what is the hot water requirement? If there is only one hand basin in need of hot water, then a single point heater will be adequate.
Alternatively, if there are two, or a single kitchen sink, then a multi-point option is more suitable.
Both heater systems are compact so can be easily installed in a kitchen cupboard or even above/under the wash unit.
Always take into account the available mains water flow rate during specification, as this can affect the delivery pressure and temperature of the water.
In addition, the flow can also be affected by the power level of the unit.
The temperature required depends on the desired use of the unit. For example, a kitchen sink will need a higher temperature than one used solely for washing hands (maximum of 41°C).
Applications such as garages and workshops, however, require slightly hotter water (ideally between 46-48°C) in order to remove oil and grease.
In all scenarios, it’s important to consider that the risk of scalding increases rapidly from the temperature of 50°C.
Also remember that the temperature from the outlet will be dependent on the mains water supply.
In summer, for example, it will be much warmer and, therefore, require less heat input than during the winter months.
This is a good point to tell customers, so they know to turn the power output down during the warmer months for water and electric cost savings.
If installing a water heater with a kilowatt rating above 3kW, it is advisable to employ a qualified electrician.
The consumer unit (fuse box) should be checked to ensure it has a mains switch rating of 80A or above and include a spare fuse way or Miniature Circuit Breaker (MCB).
In all cases, the installation, supply cable and circuit protection must conform to BS 7671 and be sufficient for the amperage required.
The unit should be situated as close as possible to the outlet to minimise any heat loss.
As such, the recommended maximum distance between the two is 0.5 metres. It also needs to be in a vertical position and connected to its own electrical circuit.
Critically, the unit should not be placed where it will be subject to freezing conditions.
The Triton Showers range of Instaflow instantaneous water heaters is available in a range of outputs including 5.4kW, 7.7kW and 10.1kW.